- 7 mm installation height
- 20 W per metre
- Copper screen
- 12-year warranty
- CE-marked in accordance with IEC 60800
|Product number||Description||100 W/m2 (C-C = 20 cm)||150 W/m2(C-C = 13,3 cm)||200 W/m2(C-C = 10 cm)||Length|
|189B2052||Veria Flexicable 20 - 200 W||2.0 m2||1.3 m2||1.0 m2||10 m|
|189B2054||Veria Flexicable 20 - 400 W||4.0 m2||2.7 m2||2.0 m2||20 m|
|189B2056||Veria Flexicable 20 - 650 W||6.4 m2||4.3 m2||3.2 m2||32 m|
|189B2058||Veria Flexicable 20 - 830 W||8.0 m2||5.3 m2||4.0 m2||40 m|
|189B2060||Veria Flexicable 20 - 970 W||10.0 m2||6.7 m2||5.0 m2||50 m|
|189B2062||Veria Flexicable 20 - 1,270 W||12.0 m2||8.0 m2||6.0 m2||60 m|
|189B2064||Veria Flexicable 20 - 1,410 W||14.0 m2||9.3 m2||7.0 m2||70 m|
|189B2066||Veria Flexicable 20 - 1,620 W||16.0 m2||10.6 m2||8.0 m2||80 m|
|189B2068||Veria Flexicable 20 - 1,890 W||18.0 m2||12.0 m2||9.0 m2||90 m|
|189B2070||Veria Flexicable 20 - 1,980 W||20.0 m2||13.3 m2||10.0 m2||100 m|
|189B2072||Veria Flexicable 20 - 2,530 W||25.0 m2||16.6 m2||12.5 m2||125 m|
|189B9240||Depron panels, 33 mm - 40 pcs.|
|189B9242||Depron panels, 6 mm - 20 pcs.|
|189B9244||Depron glue, 1 kg.|
|189B9246||Depron glue, 5 kg.|
|189B9138||VeriaFix double-sided tape|
|189B4040||Veria Control B35|
|189B4050||Veria Control B45|
|189B4060||Veria Control T45|
Veria Flexicable 20 has a continuous output of 20 W per metre, which makes it possible to achieve a heat output capable of warming even the most demanding areas, such as sunrooms, uninsulated basements, etc.
Veria Flexicable 20 should be used primarily for deep embedding projects, and it is thus well suited to new builds.
The cable can be installed directly on the substrate. The easiest way to affix it is by using VeriaFix double-sided tape or similar, although it can also be secured using a glue gun.
The heating cable is equipped with a plaited copper screen, which, via the thermostat, is connected to the earth connection of your electrical installation. Should the cable break unexpectedly, the built-in screen connection will immediately shut down the system - without any risk to people or animals.
Select the correct output
The area that a given cable can cover depends on the desired output per square metre, and thus on which c-c distance cables are installed with it.
The recommended output depends in part on the room's insulation, and partly on the floor's surface and substrate materials.
For a wooden or laminate subflooring, as well as for a wooden and laminate floor covering, a maximum output of 100 W/m² is recommended.
For a concrete or tile subflooring, as well as for a regular or quarry tile floor covering, a maximum output of 150 W/m² is recommended.
In poorly insulated areas, we recommend an output of up to 200 W/m².